hi Jignesh I was following through ur various posts on meter bypass. I have a scenario on which I would like ur valuable expert comments. I live in a multi storied government quarter. I would like to know how to bypass the single phase electronic meter. It is giving me sleepless nights. Presently both the live and the neutral from the meter goes to a MCCB which then terminates in our flats option I am considering is like using 2 wires from one live phase from main connection. One goes through the meter and other directly to the house. Since distance from the meter to our house is considerable I cannot discreetly lay a new line to the flat I plan to disconnect the neutral in the MCCB and connect the unmetered live wire to the neutral port of the MCCB. In this way 2 wires both having the same phase would be coming to my flat from a single MCCB. We have 2 separate earth connections to the flat. For neutral I plan to use the earth wire. The second earth will be used for the three pin connections so that they are secured. The metered live phase could be used for some very low load to ensure meter running for atleast the minimum units. The unmetered phase will be used for rest of the loads. My query is-
1) Will the MCCB allow 2 live connections through it (both would of same phase so no 440 volts chance)?
2) Can I install a MCB with the earth which I would using as neutral. IF so, of how much rating.
3) What safety precautions should I take for preventing electrical shocks and equipment safety.